Segregation of telecommunications and electrical cabling
Electrical contractors, electrical workers and metering providers involved in the roll out of smart meters must ensure that antenna/communication wiring systems are suitably segregated from electrical wiring in accordance with the Wiring Rules.
Wiring systems must be selected and installed in a way to avoid any detrimental effects arising between:
- electrical installations and telecommunication/data cable installations
- different electrical installations
- different parts of the same electrical installation
- circuits operating at different voltages
- circuits supplying different safety services
- safety services and the remainder of the electrical installation
- electrical installations and non-electrical installations, such as gas and water supply.
Recently, a coaxial cable was found inside a domestic electrical switchboard without suitable segregation from low voltage electrical cabling (pictured below). This presented an electrical safety risk if there was a breakdown in cable insulation. The issue was rectified following ESO enforcement action.
ESO continues to conduct audits throughout Queensland which include a focus on the installation of smart meters in residential switchboards.
For more information on electrical safety, visit electricalsafety.qld.gov.au
- Last updated
- 13 September 2019
Register for a free information session
Workplace Health and Safety Queensland in collaboration with the Australian Institute of Occupational Hygienists will deliver 10 information sessions across the state.
Lend Lease reaps benefit of helping motivated injured workers recover at work
Property and infrastructure group, Lend Lease is giving injured workers a new lease on life and rehabilitating them back to work sooner through WorkCover Queensland's Recover at Work host employment program.